Our goal is to provide you with a quick access to the content of the user manual for Toshiba T1. Using the online preview, you can quickly view the contents and go to the page where you will find the solution to your problem with Toshiba T1.
If looking through the Toshiba T1 user manual directly on this website is not convenient for you, there are two possible solutions:
Many people prefer to read the documents not on the screen, but in the printed version. The option to print the manual has also been provided, and you can use it by clicking the link above - Print the manual. You do not have to print the entire manual Toshiba T1 but the selected pages only. paper.
Below you will find previews of the content of the user manuals presented on the following pages to Toshiba T1. If you want to quickly view the content of pages found on the following pages of the manual, you can use them.
In Touch With Tomorrow
TOSHIBA INTERNATIONAL CORPORATION
13131 West Little York Road
Houston, TX 77041
PH. 800 231- 1412, 713-466-0277 FAX 713-466-8773
MODEM COMMUNICATIONS WITH THE T1 AND T2E/T2N March 1998
USING T-PDS WINDOWS FOR DIAL–UP COMMUNICATIONS WITH TOSHIBA
T1 AND T2E/T2N PROGRAMMING PORT
Stored in T-PDS
Software T1/T1S PLC
Accessories For T1 Modem Communications (with programming port): PC Side: • a standard “straight-through” 9-25 pin RS-232 serial cable; • a ≥ 9600 baud external modem. PLC Side: • a standard “straight–through” 9-25 pin RS-232 serial cable; • a “null-modem” adapter such as Radio Shack’s 9-9 pin Null Modem • a Toshiba part number TKRS232T1 T1 programming cable • a ≥ 9600 baud external modem. See Note 2 on page 5 Now that we have discussed the basic hardware requirements, let’s look at the
Click on the “Computer Link” button in the System Parameters screen, and the “ComputerLink Setup” menu will appear. Select a station number for the PLC, then click the “Communication Parameter” button . Select “NON” parity setting, and then click the “OK” buttons. When the “Write OK” screen appears, click “OK.” Now go to the PLC/Memory Management menu and select “Write to EEPROM.” The Computer Link parameters will now be stored in EEPROM memory. If you have a T2E, set the “COM” dip switch
Now let’s go to the Modem Control box and finish the T-PDS configuration. The Modem Control box is a handy database that will store a remote site name, modem initialization parameters, and the phone number of the remote site. You can move between the fields using the TAB key. The most important parameter here is the “Initialize” parameter. T-PDS will not successfully dial out or disconnect without this. The parameter shown here is the "S25” register which controls the time that the PC modem
STEP 3: CONFIGURE THE PLC’s MODEM: Now that T-PDS is configured, we are ready for the last part of our setup procedure which is to initialize our remote PLC modem. We suggest that you connect your PC to the PLC’s modem with the straight-through 9-25 pin RS-232 cable, and open up Windows Terminal (or similar). Set up the terminal program for 9600 baud, 8 data bits, 1 stop bit, no parity. Once the terminal connection is opened, you can begin to set the parameters in the PLC’s modem. There are
When the programming port is set to non parity, only the T-PDS software (and the modem) can communicate with the PLC. Furthermore, the T-PDS software must also be setup for non parity. Note 5: For T-PDS versions prior to Ver 1.2 contact Toshiba for upgrade eligibility. A SPECIAL NOTE FOR USERS THAT HAVE OLDER T1’s, T2’s, and T3’s WHOSE PROGRAMMING PORTS DO NOT SUPPORT A “NO-PARITY” SETTING If you have one of these PLCs and would like to use modem communications, you must use a modem that suppor
|3||Toshiba 5100 9||Laptop||15|