Our goal is to provide you with a quick access to the content of the user manual for Amtrol SPT-18. Using the online preview, you can quickly view the contents and go to the page where you will find the solution to your problem with Amtrol SPT-18.
If looking through the Amtrol SPT-18 user manual directly on this website is not convenient for you, there are two possible solutions:
Explore the detailed user manual for Amtrol remarkable creation, Model SPT-18. Gain valuable insights and instructions to maximize your device's capabilities and optimize your user experience. Uncover the full potential of your Amtrol SPT-18 device through this comprehensive user manual, offering step-by-step guidance and expert tips for effortless operation and enjoyment.
Many people prefer to read the documents not on the screen, but in the printed version. The option to print the manual has also been provided, and you can use it by clicking the link above - Print the manual. You do not have to print the entire manual Amtrol SPT-18 but the selected pages only. paper.
Below you will find previews of the content of the user manuals presented on the following pages to Amtrol SPT-18. If you want to quickly view the content of pages found on the following pages of the manual, you can use them.
INSTALLATION & OPERATION
West Warwick, Rhode Island 02893
Surge Arrestor SPT-7 thru SPT-70
THIS IS THE SAFETY ALERT SYMBOL. IT IS USED TO ALERT YOU TO POTENTIAL PERSONAL INJURY AND
OTHER HAZARDS. OBEY ALL SAFETY MESSAGES THAT FOLLOW THIS SYMBOL TO REDUCE THE RISK OF
PERSONAL INJURY AS WELL AS PROPERTY DAMAGE.
READ CAREFULLY THE PRODUCT INSTALLATION, OPERATING AND MA
IMPORTANT GENERAL SAFETY INFORMATION ADDITIONAL SPECIFIC SAFETY ALERTS APPEAR IN THE FOLLOWING INSTRUCTIONS solids and other relevant contaminants, including chlorine and EXPLOSION OR RUPTURE HAZARD A treat your water appropriately to insure satisfactory performance relief valve must be installed to prevent and prevent premature failure. pressure in excess of local code requirement or maximum Note: Inspect for shipping damage and notify freight carrier working pressure designated in the P
™ SIZING THE SURGE-TROL Precise Sizing For Pump Shut-down: Precise Sizing For Pump Start-up: 1 SG x 2 x Qs x L P + 14.7 /n Vv 2 Volume of Tank in Gallons = ( ) ( ) 449a P + 14.7 AF 1 Volume of Tank in Cubic Feet = 1 1 P + 14.7 /n P + 14.7 /n 2 1 -1 AF - Acceptance Factor = 1 - ( ) ( ) P + 14.7 P + 14.7 1 2 NOTE: Set pre-charge pressure 15% below static pressure. Vv - Vacuum Volume = Qss x Tc x 7.481 NOTE: To convert cubic feet to gallons mul
AMTROL INC. LIMITED PRODUCT WARRANTY Products covered: all Products manufactured by AMTROL Inc. (“AMTROL”). This warranty cannot be transferred – it is extended only to the original Purchaser or First User of the Product. By accepting and keeping this Product you agree to all of the warranty terms and limitations of liability described below. IMPORTANT WARNING – READ CAREFULLY THE INSTALLATION, OPERATING AND MAINTENANCE INSTRUCTIONS MANUAL (“MANUAL”) to avoid serious personal injury and/or pr
|1||Amtrol SPT-56 User manual||Surge Protector||0|
|2||Amtrol SPT-28 User manual||Surge Protector||1|
|3||Amtrol SPT-42 User manual||Surge Protector||0|
|4||Amtrol SPT-21 User manual||Surge Protector||0|
|5||Amtrol SPT-7 User manual||Surge Protector||0|
|6||Amtrol SPT-35 User manual||Surge Protector||0|
|7||Amtrol SPT-50 User manual||Surge Protector||0|
|8||Amtrol SPT-70 User manual||Surge Protector||0|
|9||Amtrol SPT-11 User manual||Surge Protector||0|
|10||Amtrol SPT-14 User manual||Surge Protector||3|
|11||Edelbrock 2101 User manual||Surge Protector||1|
|12||Adcom ACE-615 User manual||Surge Protector||0|
|13||Acoustic Research PW100 User manual||Surge Protector||0|
|14||Alesis 7-51-0265-A User manual||Surge Protector||2|
|15||Amtrol SPT-56 User manual||Surge Protector||0|