Our goal is to provide you with a quick access to the content of the user manual for APC CP16. Using the online preview, you can quickly view the contents and go to the page where you will find the solution to your problem with APC CP16.
If looking through the APC CP16 user manual directly on this website is not convenient for you, there are two possible solutions:
Many people prefer to read the documents not on the screen, but in the printed version. The option to print the manual has also been provided, and you can use it by clicking the link above - Print the manual. You do not have to print the entire manual APC CP16 but the selected pages only. paper.
Below you will find previews of the content of the user manuals presented on the following pages to APC CP16. If you want to quickly view the content of pages found on the following pages of the manual, you can use them.
Models: CP16 and CP27
Chapter 1: General Information ® The PowerShield provides a power source for broadband telephony, Fiber-to-the-Home/Premise (FTTH/P), and other direct current (DC) equipment/applications. Safety This manual contains important instructions that should be followed during installation and maintenance of the APC equipment and batteries. It is intended for APC customers that set up, install, relocate, or maintain APC equipment. Changes and modifications to this unit not expressly appro
Specifications General Model Number Input Output Maximum Maximum Battery Signal Signal Type Voltage Current CP16U48 100-240 V 50/60 Hz 1.0 A 48 V 30 V 5 mA 12 V 7.2 AHr 16 W Spill-Proof, Maintenance- 13 V CP27U13 100-240 V 50/60 Hz 1.0 A 30 V 5 mA Free, 27 W Sealed Lead Acid Environmental Operating Temperature -4º F to 122º F (-20º C to 50º C) Operating Humidity 5 to 95% noncondensing within enclosure Maximum Operating Elevation 10,000 ft (3,000 m) Maximum Storage Elevat
Chapter 2: Installation Enclosure Installation Install the enclosure in a protected area that is free of excessive dust and has adequate airflow. Do not operate the PowerShield where the temperature and humidity are outside the specified limits. See Indoor Use Only Specifications. ! " # Battery Cover Release Tabs $ Use screws that are appropriate for the weight of this unit and the mounting surface material. See Specifications. 3
Battery Installation ! " # Red Black Cable Cable Positive Negative Terminal Terminal Battery Cover Release Tabs $ % 4
Connect Equipment and Power The PowerShield battery charges when it is connected to utility power. The battery charges fully during the first eight hours of normal operation. Do not expect full battery run capability during this initial charge period. Utility Power Cord Inlet Output Power and Optional Runtime Communication Extension Connector Signals 1. Connect the PowerShield to the application equipment (example: FTTH/P Optical
Chapter 3: Operation Status Indicators and Features Front Panel Status Indicators Indicator Description Utility Solid green indicates the unit is on utility power. Solid yellow indicates that utility power is not present and the unit is on battery power. Flashing green LED indicates the unit is fast-charging. Green indicates the unit is working properly and DC output power is provided Output by the battery or the utility power. Replace Battery/ Red indicates that the ba
Alarm Silence Button The audible alarms may be silenced by utilizing the dual function Replace Battery/Alarm Silence LED/button / . Function Button Operation Description (Press and hold for:) Replace Battery- <4 seconds If the alarm has been silenced, the unit will emit one quick beep. If the alarm has been Temporarily enabled, two quick beeps will be emitted. Enable/Disable Replace Battery- 8-12 seconds If the alarm has been silenced, the unit will emit one quick beep. If the
Chapter 4: Maintenance, Service, Approvals, and Warranty Battery Replacement This unit has an easy to replace, hot-swappable battery. Replacement is a safe procedure, isolated from electrical hazards. You may leave the unit and connected equipment on for this procedure. During the self-test, battery removal and replacement are not recommended. For self-test disabling, see Alarm Silence Button. Replace the spent battery with APC replacement battery RBC2. See your dealer or refer to t
4. Return the unit by insured, prepaid carrier to the address given to you by Customer Support. Always DISCONNECT THE BATTERY before shipping in compliance with U.S. Department of Transportation (DOT) regulations. Contact Information Refer to the APC Web site, www.apc.com. Regulatory Approvals 9
Limited Warranty American Power Conversion (APC) warrants its products to be free from defects in materials and workmanship for a period of two years from the date of purchase. Its obligation under this warranty is limited to repairing or replacing, at its own sole option, any such defective products. To obtain service under warranty you must obtain a Returned Material Authorization (RMA) number from customer support. Products must be returned with transportation charges prepaid and mus
|1||APC CP27||IP Phone||1|
|2||Sony VERSION 1.0||IP Phone||1|
|3||321 Studios 6812D-MGCP||IP Phone||1|
|4||3Com NBX 1105||IP Phone||8|
|5||3Com NBX 2102||IP Phone||15|
|6||3Com 3107 CORDLESS||IP Phone||2|